24,000 BTU 208V/240V Portable Air Conditioning Unit - Small Server Rooms & Network Closets
Tripplite SRCOOL24K pumps 24,000 BTU of cold air into server rooms and other IT environments. Ideal for cooling a 1450 sq. ft. room, an overheated rack enclosure, or an equipment hot spot inside or outside a rack enclosure.
Provides 24,000 BTU (7 kW) of cooling capacity
Also filters and dehumidifies air
Plugs into a standard 208/240V 20A AC outlet
Restarts automatically after power failure
Can be operated remotely (requires SRCOOLNET, sold separately)
SRCOOL24K SmartRack 24,000 BTU 208/240V Portable Air Conditioning Unit
(2) Gray exhaust ducts
(2) Black cooling ducts
(2) Exhaust duct adapters
(2) Adjustable exhaust panels
(4) Self-tapping screws
Dual cooling duct adapter
Louvered vent insert(preinstalled)
(2) Drainage plugs(preinstalled)
ENVIROSENSE environmental sensor
SNMP configuration cable
Price: $5,059.80 NOW: $3,235.51 Save: $1,824.29
The SRCOOL24K SmartRack 24,000 BTU 208V/240V Portable Air Conditioning Unit pumps 24,000 BTU of cooling power into your IT environment to prevent shutdowns, malfunctions and failures caused by overheating or fluctuating temperatures. Part of the SRCOOL line, this compact, portable unit is perfect for server rooms and other IT environments with heat-sensitive equipment in areas that facility air conditioning can't reach.
The self-contained SRCOOL24K is capable of cooling a small room up to 1450 square feet using its louvered vent. A built-in evaporator expels the condensed water through the directional exhaust duct, eliminating the need for a drain tube, drain pan or water collection tank.
You can also use the included flexible tube to aim the cold air precisely where it's needed most, such as an overheated rack enclosure or an equipment hot spot. The SRCOOL24K also dehumidifies and filters the air, providing better air quality that can enhance equipment performance with little power consumption.
Designed for quick, simple installation, the SRCOOL24K rolls into place on durable built-in casters and plugs into a standard 208/240V 20A outlet. It's programmed to restart automatically after power failures, and you can set the built-in timer for unattended shutdown and startup.
By installing the optional SRCOOLNET remote management accessory (sold separately), you can also monitor temperatures, receive alerts, review logs and control settings from anywhere via SNMP, web browser, SSH or telnet.
Provides 24,000 BTU/h (7 kW) of cooling capacity in a portable chassis
Prevents equipment shutdowns, malfunctions and failures caused by overheating and temperature fluctuations
Also filters and dehumidifies the air to enhance equipment performance
Uses environmentally friendly R410A refrigerant, which complies with worldwide standards
Can cool a small room up to 1450 sq. ft.
Included 71-inch tube aims cold air where itís needed, such as an overheated rack enclosure or equipment hot spot
Built-in evaporator expels condensed water through exhaust tubeóno floor drain or water collection tank needed
Supports unattended shutdown and startup, including automatic restarts after power failures
Intuitive top-panel controls with an informative digital display and diagnostic LEDs
System-lock function disables all other buttons to prevent accidental input
Optional SRCOOLNET remote management accessory (sold separately) allows remote monitoring of temperatures, alerts, logs and control settings from any location via SNMP, web browser, SSH or telnet
Easy to Install
Rolls into place on built-in casters
A NEMA L6-20P plug connects to standard 208/240V 20A AC outlet
Includes window/drop-ceiling kit for extracting heat
No external condenser, refrigerant piping or professional maintenance required
Tripplite SRCOOL24K Specifications
Nominal Input Voltage
208V, 240V AC
2560 Watts Max
Input Connection Type
Input Cord Length (ft.)
User Interface, Alerts & Controls
Front Panel LEDs
Touch sensitive control panel with multiple LEDs and numerical temperature readout
24,000 BTU / 7 kW
56.8 L / hour
R410a (Environmentally friendly, Non ozone depleting)