Server Technology Smart PDU, 20A 208-240V 24xC13, 6xC19
note, the Server Tech CS-30V2AD25D8 has been discontinued. For other replacement options,
your Server Racks Online sales
Cabinet Power Distribution Unit with PIPS (Per Input Power Sensing).
The Server Technology CS-30V2AD25D8 Smart Cabinet Distribution Unit (CDU) provides reliable power distribution combined with local and remote power monitoring and environmental monitoring via IP. Use the network interface to view power, temperature and humidity levels via Web browser, or receive SNMP–based alarms and email alerts when conditions exceed defined thresholds.
The ServertTech Smart CDU family of products can be daisy chained together with other PDU units. The CS-30V2AD25D8 Expansion Module gives the ability to use one IP address across different power circuits.
Branch Circuit Protection The CS-30V2AD25D8 meets the UL 60950-1 requirement for Branch Circuit Protections
PIPS - Per Input Power Sensing Accurately measures Active Power, Apparent Power, Energy k-Wh, Power Capacity, and Power Capacity Used using the network interface. See the aggregate current draw, in Amps, locally using the onboard LED.
Temperature and Humidity Each Smart CDU supports two external 10' (3m) probes. A master and expansion unit allow up to four probes to meet the latest ASHRAE guidelines. Each probe measures both temperature and humidity. Receive SNMP-based alerts or emails when conditions exceed thresholds.
Linking for Smart CDU (Expansion Modules) The Server Technology Smart CDU family has the capability to daisy chain units together. The Expansion Module provides the ability to link two power circuits under one IP address.
Locking Outlets All C13/C19 outlets are fully compatible with Server Technology's locking power cords (not included).
Server Technology CS-30V2AD25D8 Specifications:
60 in. (1525 mm)
1.75 in. (44 mm)
2.25 in. (57 mm)
(24) IEC60320 C13; (6) IEC60320 C19
Nominal Input Voltage
208-240V, 50/60 Hz
IEC 320 Inlet, Bottom/Front Entry
US & Canada (cTUVs mark) to UL 60950-1:2007 and CAN/CSA 22.2 No. 60950-1-07