Designed to seal openings in new raised floor cutouts prior to the installation of communications or power cabling. Based on measurements at multiple data centers, on average 60% of valuable conditioned air is not reaching the air intake of IT equipment due to unsealed floor openings. This lost air, known as bypass airflow, contributes to IT equipment hot spots, cooling unit inefficiencies, and increasing infrastructure costs. The KoldLok 10077 specifically addresses bypass airflow and its detrimental effects on data center cooling.
Note: These KoldLok Grommets are sold as a pack of 10.
A limited quantity of single units are available.
Quantity discounts available for orders of 12+. - Please call 1-866-722-5776 to discuss single or large quantity purchases.
Price: $440.00 NOW: $330.00 Save: $110.00
Upsite Technologies 10077 Features and Benefits:
Smaller size 6” x 4” (152 x 102 mm) offers flexibility for data centers that have multiple cable opening sizes
Meets smaller cable opening standards specified in new data center builds
Cost-effective method of separating data cabling from power cabling
Contains no loose or partially fastened parts that can become separated or fall through the raised floor
The grommets are impact resistant and durable
Satisfies NFPA 75 Section 5-4.4 requirement by self-dressing the raw metal edges of raised floor tile cable openings
KoldLok products are compliant with Directive 2002/95/EC of the European Parliament and the Council on the Restriction of the Use of Certain Hazardous Substances in Electrical and Electronic Equipment (RoHS)
Increases existing cooling unit capacity
Reduces the need to purchase additional cooling units
Improves equipment reliability and extends equipment life
Increases static pressure under the raised floor and improves cool air delivery through perforated tiles and floor grates
Facilitates Cold Aisle/Hot Aisle best practices
Upsite Technologies 10077 Sealing Effectiveness:
Effective bypass-airflow sealing in areas undisturbed by cable penetrations at static pressures up to 0.10 inches of water column
Effective bypass-airflow sealing with four, half-inch cables penetrating the Grommet at a static pressure of 0.10 inches of water column