Designed to seal a wide variety of existing and new openings. Simple modification creates the flexibility to seal large and unique openings such as those found under PDUs.
Based on measurements at multiple data centers, on average 60% of valuable conditioned air is not reaching the air intake of IT equipment due to unsealed floor openings. This lost air, known as bypass airflow, contributes to IT equipment hotspots, cooling unit inefficiencies, and increasing infrastructure costs. KoldLok products specifically address bypass airflow and its detrimental effects on data center cooling.
Note: These KoldLok Grommets are sold as a pack of 10.
A limited quantity of single units are available.
Quantity discounts available for orders of 12+. - Please contact us to discuss large quantity purchases.
Price: $1,940.00 NOW: $1,358.00 Save: $582.00
Upsite Technologies 10098 Features and Benefits
The Grommets can be modified to seal unique cable openings as needed.
The Grommets contain no loose or partially fastened parts, which can become separated or fall through the raised floor.
KoldLok products are compliant with Directive 2002/95/EC of the European Parliament and the Council on the Restriction of the Use of Certain Hazardous Substances in Electrical and Electronic Equipment (RoHS).
Supports increased cabinet density
Increases existing cooling unit capacity
Reduces the need to purchase additional cooling units
Improves IT equipment reliability and extends equipment life
Increases static pressure under the raised floor and improves cool air delivery through perforated tiles and floor grates
Compliance with best practices for all raised floor cooling configuration (Hot and Cold Aisle, Hot Aisle containment, Cold Aisle containment, etc.)
Upsite Technologies 10098 Sealing Effectiveness
Effective bypass airflow sealing in areas undisturbed by cable penetrations at static pressures up to 0.10 inches of water column
Effective bypass airflow sealing with four ½ inch cables penetrating the Grommet at static pressure required to cool up to 3 kW/cabinet
Effective bypass airflow sealing with four ½ inch cables penetrating the Grommet at a static pressure of 0.50 inches of water column